Payment & Shipping Terms:
|Uc (DC):||48V||Protection Mode:||+/PE,-/PE|
Upplugged power surge protector with built-in over current breakers
|Protection Class||Type 2|
|Working Voltage Un(DC)||48V|
|Max. Continuous Operating Voltage Uc(DC)||150V|
|Nominal Load Current||60A|
|Nominal Discharge Current(8/20μs)(In)||5KA|
|Max. Discharge Current(8/20μs)(Imax)||10KA|
|Voltage Protection Level( Up)||1.5KV|
|Working Environment||Temperature -40°C~+80°C;Relative humidity<95%|
|Material of Outer Shell||Flame retardant materials|
Product diagram & dimention
The SPD connected in parallel with the power lines, installed by the way of 35 mm leading rail.
When installed, in and out terminal of SPD will be corresponding connected with"+","-"pole of the DC power; "PE" is connected with grounding line; Connection way is by screwing tightly.
All wires must be solid and connected by electrics cable. SPD cable: BVR≥2. 5mm2.
Grounding of lightning protection should comply with the lightning protection standard; grounding wire should be as thick and short as possible, ground resistance should be less than 4Ω. The grounding wire of SPD reliable connected with the grounding row of lightning protection system, after installation finished, check the wires if correct, switch on, then the SPD can be put into use.
Contact Person: Lili Ling